The vector group of transformeris an essential property for successful parallel operation of transformers.
Hence every electrical power transformer must undergo through vector group test of transformer at factory site for ensuring the customer specified vector group of transformer, JYT-F transformer turn ratio tester has this function.
The phase sequence or the order in which the phases reach their maximum positive voltages, must be identical for two paralleled transformers. Otherwise, during the cycle, each pair of phases will be short circuited.
The several secondary connections are available in respect of various primary three phase connection in a the three phase transformer. So for same primary applied three phase voltage there may be different three phase secondary voltages with various magnitudes and phases for different internal connection of the transformer.
Before transformer turn ratio tester test vector group of transformer, let's have a discussion in detail by example for better understanding.
We know that, the primary and secondary coils on any one limb have induced emfs that are in time-phase. Let's consider two transformers of same number primary turns and the primary windings are connected in star. The secondary number of turns per phase in both transformers are also same. But the first transformer has star connected secondary and other transformer has delta connected secondary. If same voltages are applied in primary of both transformers, the secondary induced emf in each phase will be in same time-phase with that of respective primary phase, as because the the primary and secondary coils of same phase are wound on the same limb in the core of transformer. In first transformer, as the secondary is star connected, the secondary line voltage is √3 times of induced voltage per secondary phase coil. But in case of second transformer, where secondary is delta connected, the line voltage is equal to induced voltage per secondary phase coil. If we go through the vector diagram of secondary line voltages of both transformer, we will easily find that there will be a clear 30oangular difference between the line voltages of these transformers. Now, if we try to run these transformers in parallel then there will be a circulating current flows between the transformers as because there is a phase angle difference between their secondary line voltages. This phase difference can not be compensated. Thus two sets of connections giving secondary voltages with a phase displacement can not be intended for parallel operation of transformers.
JYT-F transformer turn ratio tester has vector group test function which can show vector group very clear, for more information please log on our production page for checking.